Sat Nov 24, 2007 7:46 pm
technova wrote:Anyone know what the air pressure is supposed to be?
It is a maroon tank from Menard's don't remember the brand
or required pressure. I'm at work, can get the brand tonite if necessary.
It's the cold water so the heater is not compounding the problem if it's trapped air.
Mon Feb 11, 2008 9:43 pm
Eugene wrote:Pump in the well sucking air?
Tue Feb 12, 2008 8:29 pm
Wed Mar 05, 2008 9:25 am
Sat Apr 26, 2008 6:12 pm
Mon Apr 28, 2008 7:46 pm
Tue Apr 29, 2008 8:33 am
Thu May 01, 2008 8:41 am
Sat May 03, 2008 6:02 pm
Sat May 03, 2008 8:11 pm
schmibm wrote:I don't think the chlorine did anything to keep the rust out of the toilet. The filter must be doing that. Iron in the water will cause this. A water softener is the treatment unless it is real bad.
What you did with the chlorine was kill the bacteria in the system. Should be done every so often with a well.
Sat May 03, 2008 9:24 pm